Photo Gallery:New Organs
Articles:Pipe Organ Standards
When is a Pipe Organ
NOT a Pipe Organ?
What is a Combination
Organs and Temperature
Organs and Lightning
Pipe Organ Builder
Contact Us:Contact Details
PO Box 838
Lithonia GA 30058
While not all inclusive, this document serves as a general statement on lightning and its affect on pipe organ relays, combination actions, MIDI devices, and amplifiers, as well as associated digital voice generators and power sources of DC (direct current) rectifiers.
Millions of dollars worth of damage, and in some cases complete loss of equipment and structures, are a result of lightning in public assembly buildings. Much research has been conducted on ways to lessen the effects of lightning, as well as the effects of Electromagnetic Interference (EMI), to the electronic systems that may be utilized in the modern pipe organ.
Lightning is a natural event. The lightning bolt appears to be indiscriminate in nature and can choose to strike anything at random. However, it only takes one strike in the vicinity to create havoc within today's pipe organs.
Each damaged instrument can be subject to both immediate documented problems, and conditions where components are weakened but may not cause immediate problems. Failure can occur up to a year after the lightning or EMI event. It should be noted that any semi-conductor that lightning comes close to can be affected. Lightning is always seeking ground to complete the circuit. Conductive material such as a copper roof, bell tower, and conductors in the attic will act as a lightning rod, particularly if it is connected to anything which may provide a path to earth ground.
Lightning strikes, effects of EMI, and electromagnetic pulses resulting from airborne radiation, can effect nearby semi-conductor components. The results of damage are usually immediate, but may become evident anytime within up to one year of the event. Damage can vary greatly from a few components, to the destruction of every component within a relay, combination system or any electronic system or subsystem.
The following list, while not complete, describes ways that lightning damage occurs:
I will not detail every aspect of how and why organs are affected by the four above categories. I will however provide the following general details as to the cause and effect.
Although the major focus of this document is lightning, its effects can result in similar effects of electrical (AC or DC) surges of power and amplified signals associated with the transmission of energy, i.e. surge.
The modern pipe organ is supplied DC current from a rated and listed rectifier that is over-current protected. Providing protection from lightning and power surges can be quite challenging, as 220V or 220/440V three-phase power supplies are the source of AC current for many larger systems.
Some churches and public assembly places have installed line voltage conditioners, which have fail-safe engineering to restructure the line voltage for the organ. These devices can provide a higher level of protection against the power line pulse that can occur from a lightning event. This is very expensive and has proven to be only marginally effective, because lightning does not affect the pipe organ from only the power source.
In repairing a damaged pipe organ, reference should be made to the International Electrical Code/National Electrical Code, which is a division of the National Fire Protection Association, to assure that all repairs, wiring and over-current protection is in compliance with these codes. The repairs should also be in compliance with all local, county, or state agencies which have jurisdiction for the installation or modification of low-voltage 0-50 volt AC or DC, and AC or DC power circuits for 50 volts or higher. Any work on the high or low voltage circuits that require modification, change, or servicing of such circuits, should only be carried out with whatever permits or licenses are required from the city, county, or state which has jurisdiction
Although the NEC pipe organ code (Article 650 Pipe-Organ) does not give specific information on lightning/electrical surges, the National Electrical Code does provide guidance in Article 285, Article 640 and Article 501, as well as articles dealing with low-voltage and general conductor and wiring practices. Although Article 650 deals specifically with the wiring of a pipe organ, it should be noted that all other articles of the code also apply, depending on the circumstances, such as in electronic sound generating equipment, speakers, amplifiers, etc., per Article 640, as well as the installation within a Public Assembly Place, Article 518.
The pipe organ code (Article 650) is very explicit about the installation of power signal circuits and wire size, as well as over-current protection and installation of rectifiers and blowers. The use of electronic equipment, such as MIDI equipment, electronically generated organ sounds, amplifiers, speakers, and associated wiring, is to comply with Article 640.
This document is not a substitute for a review of each institution, and compliance with its code. However, listed below are a few of the items that should be reviewed.
NOTE: This document has been compiled for reference purposes using information from public domain sources, and Code material from the National Electrical Code. The author of this document, Arthur E. Schlueter, Jr. is a member of Panel 12 of the National Electrical Code. This document is copyrighted by A.E. Schlueter Pipe Organ Company, 2008-2012 and may not be copied or reproduced without permission.
To inquire about possible lightning damage to a pipe organ, give us a call at
800-836-2726 or 770-482-4845.
Copyright 2006-2017 All Rights Reserved by A.E. Schlueter Pipe Organ Co., Inc.
David Kocsis Web Master